- 28/Sept, 2018
6 Common Mistakes to avoid in Telecom Technology Grounding: Electrical Safety Rules
All electrical systems and communication cabling systems are required to be grounded. This is required to provide a reliable means to safely conduct the voltages imposed by lighting, line surges, or unintentional contact with high voltage lines or equipment to ground. Similarly, telecommunication networks and equipment should be grounded to the electrical service. However, simply grounding to structural steel is not enough when dealing with telecommunication systems. The sensitivity of the electronic equipment requires that the telecommunications cabling and power be effectively equalised to prevent loops or transients that can damage the equipment. This means designing a complete grounding and bonding system that goes beyond the basic methodology.
Surge protection failures are costly. It leads to damage or destruction of expensive technology, downtime as well as customer dissatisfaction. Most companies, educational institutes, hospital, commercial complexes or any networked building, house valuables and sensitive telecommunication equipment. A good quality surge-protection technology is a must to ensure that external surges cannot damage their equipment. True surge protection begins from the ground up. Not even top-of-the-line surge protectors can protect valuable and sensitive telecom equipment if the protector is not properly grounded.
The following six grounding mistakes are responsible for a vast majority of surge-protection failures:
When technicians instal a surge protector- they use an impedance of not more than 8 to 15 ohms. However, for the protection of sensitive digital telecom equipment used to send and receive data or voice, such as computers, phones, Ethernet Voice over IP, T1/E1, ISDL and DSL, installers should make sure there are common grounding and ground potential of less than 1 ohm-ideally less than 0.5 ohm.
Wrapping Ground Wire
Many installers bring lengthier than required cabling and end up often coiling the additional wire. Coiling the wire significantly increases resistance and can lead to malfunctioning surge protection and profoundly impacting the effectiveness of the surge-protection technology.
As a rule of thumb, not only should cable never be coiled, it should always be installed in as straight a manner as possible. Any minor bends or loops can add dangerous resistance.
Size of Wire
The thicker the wire gauge, the lower its resistance, which is good as lower resistance allows for the unhindered transmission of the surge to the ground. Selecting which gauge of wire that will not only meet your needs today- but even when more advanced technologies will likely need to be added to your grounding platform. It is always better to instal a thicker gauge wire to ensure that your technology is well grounded today and in the years ahead as well.
Incorrect Way of Wire Connections
The wire used to connect the electric copper ground rod to the telecommunications room common busbar needs to be securely tied down with a spade or ring lug. If the joints in the grounding setup are not fastened tightly enough, extra resistance, known as contact resistance, is generated; it can reduce the effectiveness of surge-protection equipment.
It is crucial to identify a technology that minimises the chances for installation errors to occur. It is important that your surge connector comes with all of the hardware necessary for proper grounding so that precisely the correct parts are used by the installer. Also, look for technologies that minimise the need to do additional grounding when new technologies are added.
Lack of a Single Grounding Point
Protector ground and all other equipment grounds that are being protected must be connected to a “single common ground point.” A single ground point balances the ground resistance. If more than one single common ground point is used, surge and lighting can travel from one ground point through the equipment to the other ground point. This process is called “ground loop” and can damage the equipment.
20/ 06, 2019 Pedestal fans are nothing but portable electric fans. They are electrically-powered devices that are used to circulate a cool breeze around your home. The weather in tropical countries like India can get extremely hot and humid, which is why investing a soothing ventilation system such as a pedestal fan can be very […]
20/ 06, 2019 Telephones are an important invention that have the ability to connect people all over the world. They consist of numerous pairs of copper insulated wires having a diameter that ranges from 0.3 to 0.9 and are either twisted into two or four pairs. These pairs of wires are then connected to each […]
31/ 05, 2019 It is safe to say that in today’s digital age, wired connections have taken a back seat. They are often synonymous with clutter and inconvenience, creating a mirage of limitations that tend to camouflage their benefits. However, when it comes to the aspect of functionality and security, wired broadband is still remains […]
31/ 05, 2019 Summer is at its peak in India, and the last thing you need is your air conditioner switching off and tripping the circuit breaker. If this happens to your air conditioner frequently, you may be wondering how to rectify the situation. Let’s first take a look at the role your AC circuit […]
31/ 05, 2019 There is no doubt that a safe workplace ensures a safe workforce – and the one aspect that plays a big role in safety at work is the use of right electrical switches. This is especially true when you are dealing with a small workspace where the switches are used frequently and […]