- 28/Sept, 2018
6 Common Mistakes to avoid in Telecom Technology Grounding: Electrical Safety Rules
All electrical systems and communication cabling systems are required to be grounded. This is required to provide a reliable means to safely conduct the voltages imposed by lighting, line surges, or unintentional contact with high voltage lines or equipment to ground. Similarly, telecommunication networks and equipment should be grounded to the electrical service. However, simply grounding to structural steel is not enough when dealing with telecommunication systems. The sensitivity of the electronic equipment requires that the telecommunications cabling and power be effectively equalised to prevent loops or transients that can damage the equipment. This means designing a complete grounding and bonding system that goes beyond the basic methodology.
Surge protection failures are costly. It leads to damage or destruction of expensive technology, downtime as well as customer dissatisfaction. Most companies, educational institutes, hospital, commercial complexes or any networked building, house valuables and sensitive telecommunication equipment. A good quality surge-protection technology is a must to ensure that external surges cannot damage their equipment. True surge protection begins from the ground up. Not even top-of-the-line surge protectors can protect valuable and sensitive telecom equipment if the protector is not properly grounded.
The following six grounding mistakes are responsible for a vast majority of surge-protection failures:
When technicians instal a surge protector- they use an impedance of not more than 8 to 15 ohms. However, for the protection of sensitive digital telecom equipment used to send and receive data or voice, such as computers, phones, Ethernet Voice over IP, T1/E1, ISDL and DSL, installers should make sure there are common grounding and ground potential of less than 1 ohm-ideally less than 0.5 ohm.
Wrapping Ground Wire
Many installers bring lengthier than required cabling and end up often coiling the additional wire. Coiling the wire significantly increases resistance and can lead to malfunctioning surge protection and profoundly impacting the effectiveness of the surge-protection technology.
As a rule of thumb, not only should cable never be coiled, it should always be installed in as straight a manner as possible. Any minor bends or loops can add dangerous resistance.
Size of Wire
The thicker the wire gauge, the lower its resistance, which is good as lower resistance allows for the unhindered transmission of the surge to the ground. Selecting which gauge of wire that will not only meet your needs today- but even when more advanced technologies will likely need to be added to your grounding platform. It is always better to instal a thicker gauge wire to ensure that your technology is well grounded today and in the years ahead as well.
Incorrect Way of Wire Connections
The wire used to connect the electric copper ground rod to the telecommunications room common busbar needs to be securely tied down with a spade or ring lug. If the joints in the grounding setup are not fastened tightly enough, extra resistance, known as contact resistance, is generated; it can reduce the effectiveness of surge-protection equipment.
It is crucial to identify a technology that minimises the chances for installation errors to occur. It is important that your surge connector comes with all of the hardware necessary for proper grounding so that precisely the correct parts are used by the installer. Also, look for technologies that minimise the need to do additional grounding when new technologies are added.
Lack of a Single Grounding Point
Protector ground and all other equipment grounds that are being protected must be connected to a “single common ground point.” A single ground point balances the ground resistance. If more than one single common ground point is used, surge and lighting can travel from one ground point through the equipment to the other ground point. This process is called “ground loop” and can damage the equipment.
Modular Colour Plates Add To Your Home Decor Modular plates are the coverings on your electrical switches. Their main purpose is to keep wires out of sight, and to keep you safe. These plates have evolved over the years to be more in tune with interior designing trends. Earlier, the décor of a room could […]
LED Lighting Trends For 2020 It is not only a new year but a new decade. The modern home and how people live is constantly evolving. Lighting today is a matter of interior design, illumination, productivity, environment and pricing. The successful transition to LEDs has seen light ambience ranging from warm to cool, from ideal […]
10 Décor Ideas To Try In 2020 31/ 01 /2020 You might want to upgrade your home, remodel, or you’re simply moving into a new place. The start of the year is a great time to set the mood for the decade. The year 2020 is set to bring some interesting trends for home décor. […]
26/ 12 /2019 A ceiling fan isn’t meant to just keep a room cool. It can be decorative & even help make your cooling systems more efficient. There are lots of choices available for today’s homeowners. There are even great options available for installations in large halls or businesses. It can be a little intimidating […]
10/ 12 /2019 Here’s How You Can Choose A LED Light That Saves Money When you’re setting up your dream home you want to have the best décor, appliances & fittings. The right lighting can make a great difference for new homes, renovated homes, or even when you are carrying out minor improvements. Ideal lighting […]